Writer： Kaiqian Oil Purifier Release time：2018-07-01 00:00 Clicks：
All parts of the transformer oil purifier have passed the commissioning and operation test before leaving the factory. When it is transported to the use site, it is necessary to check whether all parts are intact.
In the treatment of the oil tank of the generator set, the settling water at the bottom of the oil tank shall be drained before connecting the oil pipe, otherwise the settling water will enter the oil filter and cause secondary pollution. When the vacuum pump of the transformer oil filter works, pay attention to the oil indicated by the oil level indicator (the oil should be on the oil level indicator line), and replace it in time when there is much water in the vacuum pump oil.
When there is condensate on the liquid level pipe of the cooler, it shall be discharged in time (close the oil filter, release the vacuum, and then open the valve at the lower end of the cooler to drain the condensate). During the operation, pay attention to whether the vacuum pump and corresponding operation noise are normal at any time, and eliminate the abnormal immediately. When the oil intake is insufficient, stop the machine to check whether the primary filter element and secondary filter element are blocked by impurities. If they are blocked by impurities, remove the primary filter element, secondary filter element and tertiary filter element for cleaning.
Address：No.66 Kecheng Road,Jiulongpo District, Chongqing, China